This updated advisory is a follow-up to the updated advisory titled ICSA-19-085-01 Siemens SCALANCE X (Update A) that was published June 11, 2019, to the ICS webpage on us-cert.gov.
Successful exploitation of this vulnerability could allow an attacker to feed data over a mirror port and into the mirrored network.
The following SCALANCE products are affected:
--------- Begin Update B Part 1 of 3 --------
--------- End Update B Part 1 of 3 ----------
The monitor barrier of the affected products insufficiently blocks data from being forwarded over the mirror port and into the mirrored network. An attacker could exploit this vulnerability to transmit malicious packets to systems in the mirrored network to influence their configuration and runtime behavior.
This vulnerability could be exploited by an attacker with network access to the traffic-receiving network. Successful exploitation requires no system privileges and no user interaction. An attacker could use the vulnerability to compromise the confidentiality and availability of the traffic-generating network.
Siemens reported this vulnerability to CISA.
--------- Begin Update B Part 2 of 3 --------
Artem Zinenko of Kaspersky identified that SIPLUS is also affected.
--------- End Update B Part 2 of 3 --------
Siemens has provided the following specific updates that users can implement to mitigate this vulnerability:
--------- Begin Update B Part 3 of 3 --------
--------- End Update B Part 3 of 3 ----------
Siemens has identified the following specific workarounds/mitigation that users can implement to reduce the risk:
As a general security measure, Siemens strongly recommends users protect network access to devices with appropriate mechanisms. In order to operate the devices in a protected IT environment, Siemens recommends users configure the environment according to Siemens’ operational guidelines for Industrial Security, and follow the recommendations in the product manuals.
Additional information on industrial security by Siemens is available at: <https://www.siemens.com/industrialsecurity>
For further inquiries on security vulnerabilities in Siemens products and solutions, please contact Siemens ProductCERT
For more information on this vulnerability and more detailed mitigation instructions, please see Siemens Security Advisory SSA-557804
CISA recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.gov in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
This vulnerability requires high skill level to exploit. No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
For industrial control systems cybersecurity information: https://www.us-cert.gov/ics
or incident reporting: https://www.us-cert.gov/report
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.
This product is provided subject to this Notification and this Privacy & Use policy.
Was this document helpful? Yes | Somewhat | No