ICS-CERT originally released advisory “ICSA-11-335-01P - 7-Technologies Data Server Denial of Service” in the US-CERT secure portal on December 01, 2011. This web page release was delayed to allow users time to download and install the update.
Security researcher UCQ from the Cyber Defense Institute, Inc. has identified a buffer overflow vulnerability in the 7-Technologies (7T) IGSS Data Server application.
ICS-CERT has coordinated with 7T, which has produced a patch to resolve this vulnerability. The Cyber Defense Institute, Inc. has tested the patch and confirmed that it resolves the reported vulnerability.
Version 188.8.131.5200 of 7T IGSS Data Server is affected.
Successful exploitation of this vulnerability can allow an attacker to execute a remote denial of service (DoS) against the 7T data server on the targeted host computer, resulting in adverse application conditions.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
7T, based in Denmark, creates monitoring and control systems that are used primarily in the United States, Europe, and South Asia. According to the 7T website, IGSS has been deployed in over 28,000 industrial plants in 50 countries worldwide.
The 7T IGSS human-machine interface (HMI) is used to control and monitor programmable logic controllers (PLCs) in industrial processes across multiple sectors including energy, manufacturing, oil and gas, and water.
This vulnerability can be exploited by sending a specially crafted packet to Port 12401/TCP. A successful exploit will cause a buffer overflow that can result in a remote DoS against the 7T Data Server application on the targeted host.
CVE-2011-4050 has been assigned to this vulnerability.
This vulnerability is remotely exploitable.
No known public exploits specifically target this vulnerability.
An attacker with a moderate skill level can exploit this vulnerability.
7T has developed a patch to address this vulnerability and has provided the following options to customers who wish to update their systems:
Instructions: Browse to the 7T IGSS website. From the “Download” menu select the “Licensed Versions” option. From this page, select the Version 9 “Program updates (General)” to download a ZIP file containing all current updates for IGSS Version 9. Once the ZIP file (progupdatesv90.zip) has downloaded, manually unpack the ZIP file, and copy the entire contents to the \IGSS\ directory within the IGSS installation folder on the end user’s computer.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
The Control Systems Security Program (CSSP) also provides a section for control system security recommended practices on the CSSP web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.